Arc Flash Analysis Program
What is Arc Flash?
See a video about what happens during an electrical arc flash.
NFPA standard 70E requires electrical equipment owners to perform arc flash hazard analysis to determine the arc flash boundary, the incident energy at the working distance, and the personal protective equipment (PPE) that workers within the arc flash boundary must use. PPE is not intended to prevent all injuries, but is intended to mitigate the impact of an arc flash, should one occur.
How Do We Avoid Arc Flash at The University of Texas at Austin?
- Trained facilities personnel should de-energize the equipment affected and perform proper lockout/tagout procedures whenever possible.
- Energized work is prohibited on exposed electrical parts with nominal voltage of more than 50 volts, unless workers are conducting tests or trouble-shooting where de-energizing is not feasible, or unless de-energizing the part(s) will create a greater hazard.
- Only qualified persons shall be permitted to work on electrical conductors or circuit parts that have not been put into an electrically safe work condition.
- Those working on or near exposed energized electrical parts shall use appropriate personal protective equipment (PPE) and tools to protect themselves from potential electrical shock, arc flash, and fire hazards.
See PPE Category Information HERE.
What is Arc Flash Analysis?
The arc flash analysis must be updated when a major modification or renovation takes place. It must be reviewed periodically, not to exceed five years, to account for changes in the electrical distribution system that could affect the results of the arc flash hazard analysis.
Why is an Arc Flash Analysis Program Required?
The guidelines for work involving electrical hazards and the selection of arc flash protective equipment are provided by National Fire Protection Association (NFPA) standard 70E. This standard requires electrical equipment owners to perform arc flash hazard analysis to determine the arc flash boundary, the incident energy at the working distance, and the personal protective equipment (PPE) that employees within the arc flash boundary must use.
The arc flash analysis must be updated when a major modification or renovation takes place. It must be reviewed periodically, not to exceed five years, to account for changes in the electrical distribution systems that could affect the results of the arc flash hazard analysis.
The standard for calculating arc flash energy levels at different points in the electrical power system is provided by Institute of Electrical and Electronics Engineers (IEEE) standard 1584.
Click HERE to see The University of Texas of Austin's standard operating procedures for Arc Flash Analysis and Documentation.
Arc Flash Analysis Progress at UT Main CampusProgress on Arc Flash Analysis on the university's Main Campus is provided in a quarterly report, prepared by the AFAP Team:
- Arc Flash Quarterly Report FQ3 2013-2014
- Arc Flash Quarterly Report FQ2 2013-2014
- Arc Flash Quarterly Report FQ1 2013-2014
- Arc Flash Quarterly Report FQ4 2012-2013
Arc Flash Analysis Labels
- Equipment designation
- Nominal voltage
- Flash protection boundary
- Hazard risk category
- Incident energy
- Working distance
- PPE required
Here is an example:
Roles and Responsibilities
- Implement arc flash studies that are lacking on existing buildings at the university's Main Campus and J. J. Pickle Research Campus.
- Maintain copies of documents and electronic files for site studies. This includes copies of all short-circuit coordination studies, arc flash studies, and single-line diagrams, as well as documentation on subsequent electrical system changes.
- Implement a five-year electrical single-line (power-flow study) review.
- Ensure respective employees comply with all provisions of the Arc Flash Analysis Program.
- Ensure respective employees are trained in arc flash and electrical safety.
- Assist arc flash analysis team in a five-year review and update of existing arc flash analysis.
- Report to the Primary AFAP Engineer any discrepancies between field conditions and the single-line diagram created with SKM Systems Analysis, Inc. (SKM) electrical engineering software.
- Coordinate with the Primary AFAP Engineer to maintain up-to-date single-line diagrams, panel schedules, and SKM models.
- Include a review of the arc flash study in any major modification or renovation to the electrical system of a building.
- Deliver reviewed and completed SKM files and other electrical power system documentation to the Primary AFAP Engineer as part of the project sign-off.
Arc Flash Analysis in Project Management - Flow Chart
Click HERE to view a flow chart that illustrates the process used to determine when project managers should incorporate arc flash analysis into the scope of projects at the university.
Arc Flash Analysis Program - University ContactsFor questions or additional information about the university's Arc Flash Analysis Program or the content provided on this page, please contact:
- Darnell Mack, P.E.
Engineering and Technical Support
Facilities Operations and Maintenance, Facilities Services
For questions or information regarding the university's facilities-related safety programs, please contact Jennifer Root, Safety Manager, at firstname.lastname@example.org or call her direct line at (512) 471-3292.